- Environment & Conservation
- Construction & Development
- Businesses & Key Accounts
- Help & FAQs
- About Us
Installation Requirements for Water Service
We must inspect the entire length of water service piping outside the building before you cover it. This includes water service piping that is:
- Newly installed
If your piping is covered before inspection and approval, you must uncover it in its entirety. We can’t accept pictures or videos.
When you’re ready for an inspection, call to request a same-day inspection:
- Between 8:00 a.m. - 9:00 a.m., call (206) 684-5803
- After 9:00 a.m., call (206) 684-5800
An inspector will visit the site on the same day, depending on availability.
After the inspection is complete:
- The inspector will provide a “Utility Service Inspection Report” (a yellow card) detailing the results.
- The inspection report will be left on the front door or at other weather-protected locations like a meter box or other easily accessible enclosure.
If you’re using water service piping for fire protection:
- You must also call The Seattle Fire Department at (206) 386-1443 for an inspection.
An SPU backflow inspector must also inspect of the fire system’s backflow assemblies. Please call (206) 684-3536 to schedule the backflow inspection.
You may be charged a re-inspection fee of $50 if:
- The site is not accessible to the inspector upon arrival.
- The inspection can’t be completed because the location requiring inspection is not reasonably or safely accessible by the inspector upon arrival.
- The water line is under water or covered by other objects or materials.
- You ask for an inspection and the work isn’t complete.
- Corrections requested after a previous inspection haven’t been made.
Requirements for underground water lines
- All work must be performed in compliance with the current Uniform Plumbing Code.
- Connection of customer’s pipe must be to the city’s union only.
- Outside service pipe must have no less than 2-feet of earth cover from all angles and at all points.
- Water pipe and fittings must be brass, copper, DI, SS, CPVC, HDPE, PE, PEX or PVC manufactured to recognized standards for cold water distribution systems outside buildings.
- Copper must have a weight of Type L or K.
- Plastic pipe must be a minimum of schedule 40, 160 PSI.
- All piping must have an NSF or ASTM stamp approval.
- All building supply pipe must be ¾-inch or larger.
- Plastic pipe, not approved through the foundation, will need pipe studded out 2-feet of an approved material.
- All plastic pipes must have a blue insulated copper tracer wire or other approved conductor that terminates at each end of the nonmetallic piping above ground (UPC code #604.8).
- Tracer wire must be no less than 18 AWG and insulation must be suitable for direct burial.
- Property’s water piping must extend beyond any slope, embankment, rockery, bulkhead or fence to the city’s service. No service line (new or abandoned) is to be used as an electrical ground.
- Where local static water pressure is more than 80 PSI, an approved pressure regulator must be installed.
- Shutoff valve controlling all outlets of each building must be installed on property.
- All irrigation system connections must have a shutoff valve and approved backflow protection.
- All required shutoff valves shall be accessible.