Underground electric cable in View Ridge was buried directly in the ground from 1969 to 1974 using the technology and materials available at the time. As underground cables age, the protective insulation deteriorates. In 2009 and 2010, Seattle City Light tested and, where possible, injected the cable with silicon. The silicon injection process extends the life of the cable by at least 20 years. Approximately 60 percent of the cable that was tested was injected. The other 40 percent of the cable in the neighborhood was tested but found not suitable for injection. That 40 percent must now be replaced. The next step in replacement is installation of conduit. Seattle City Light is hiring a contractor to install conduit and associated work, including new electrical vaults; curb ramp installation and restoration, sidewalks, pavement, and landscaping. The final step will be pulling the cable into the protective conduit by Seattle City Light crews.
In 2012, test holes were drilled to determine the location of other utilities that are near where the conduit will be installed. The conduit will be installed by tunneling beneath the ground's surface. This method is called horizontal-directional drilling (HDD). HDD is much less disruptive to sidewalks and landscaping than open trenching. It is also a less expensive, faster means of replacing the electrical system. City Light's Resident Engineer will be on-site to monitor the contractor.
The status of your electric cable may have changed due to the need to make emergency repairs since the original silicon injection project. A map showing the locations where new conduit and vault installations are necessary can be found here.
City Light welcomed View Ridge residents to its Dec. 17 community meeting. Attendees were able to:
- Learn more about upcoming construction activities
- Speak with City Light staff
- Meet the contractor
During the week of 12/23, customers in the Sand Point Country Club neighborhood will begin to see locate marks and flags. These markers help crews stay safe and protect against drilling into other utilities. We ask that the painted marks not be pressure washed and the flags not be moved. The locate paint will fade with time and weather.